The little green control modules, called frogs, are the heart of every frogblue system and form the basis of frogblue's Bluetooth®-based smart building solution. Our frogs switch, dim, measure, open doors or respond to buttons, switches and window contacts.
Connected to the mains or battery-powered, they establish "virtual cables" between each other via the frogblue Bluetooth® mesh network, relaying messages and extending their range. Data transmission between the frogs is exclusively encrypted (128-bit), in addition to Bluetooth®. Frogs are smart, bursting with innovative features, easy to configure and do not require a central processing unit or control cabinet. With a power consumption of only 0.2 watts, they are also exceptionally energy-conscious.
Installed in the deep flush-mounted box (recommended box depth: 63mm) behind any conventional switch/button, junction box, weatherproof outdoor box or lamp outlet, this multifunctional 1-channel dimming actuator can be used to switch and dim all lamps approved for phase control. Phase angle control is only permitted for inductive loads.
Temperature cut-out (>75 °C)
Feedback for switching status and dimming value.
Parametrisable switching on behaviour and dimming behaviour
Switching on and switching off delay with switching off warning
Mains supply via power cable, no additional cabling required between frogblue modules.
Phase cutting or phase section control can be switched via the frogblue app (phase cutting control only permitted for inductive loads)
For assembly in device sockets according to DIN 49073. Socket depth minimum 53 mm when installed behind switch insert, individual installation is required at lower depth.
This device is a product of the frogblue system. Detailed technical expertise obtained through frogblue training sessions is a prerequisite. The functionality of the device depends on the software. Detailed information regarding software versions and the respective range of functions can be found on the frogblue website. Technical descriptions, additional detailed instructions as well as notes, information regarding proper disposal can be found in the manual, which is available on the frogblue website. Commissioning and configuration will be executed using the frogblue app.
Electrical devices may only be installed and assembled by qualified, skilled electricians. Failure to observe the instructions can cause damage to the device and result in fire and other hazards. Danger caused by electric shock. Device is not suitable for disconnection from power voltage. Even when the device is turned off, the load is not electrically isolated from the mains. Before starting work on the device or replacing light sources, always disconnect the power supply and switch off the circuit breakers. Country-specific regulations must always be observed.
Once the user has seen at least one product this snippet will be visible.
Recently viewed Products
To install this Web App in your iPhone/iPad press and then Add to Home Screen.