Multifunctional 2-channel relay switch with 2 potential-free outputs. With 2 inputs to query buttons and switches (110-240 V ~). Featuring integrated logic module with comfort and timer functions and power measurement.1
The small green control modules, called frogs, are the heart of every frogblue system and form the basis of the Bluetooth®-based smart building solution from frogblue. Our frogs can switch, dim, measure, open doors or react to buttons, switches and window contacts.
Connected to the mains or battery-powered, they are linked together with “virtual cables” via the frogblue Bluetooth® mesh network. They forward messages and thus extend the range. Data transfer between the frogs is always encrypted (128 bit), and this in addition to Bluetooth®. frogs are smart, packed with innovative functions, are very easy to configure and do not require a central unit or control cabinet. With a power consumption of just 0.2 watts, they are also extraordinarily energy-conscious.
Installed in a deep flush-mounted back box (recommended socket depth: 63 mm) behind any conventional switch/button, junction box, weatherproof outdoor socket or roller shutter housing, this multifunctional 2-channel relay switch with two potential-free outputs and two inputs can primarily be used to for controlling shade, e.g. blinds, roller shutters, roller blinds, awnings or the pool cover without new cables. All over the building and from anywhere.
Shade can also be controlled fully automatically via user-defined time programs. The same applies in combination with the frogDisplay and its Astro function, with which you can start the day by automatically opening the slats when the sun rises.
The frogblue relay modules are designed for controlling 1200 W per channel. In addition to the shade control, other appliances can also be switched via the frogRelay2-2-PF. For example, the garage door or LED strips with a larger power consumption.
By utilising the free input channels of other frogs contained in the system, external sensors, such as a wind monitor or a weather station can be integrated. In the event of a storm, the blinds are raised automatically and cannot be lowered manually. Alternatively, they can be automatically lowered when the sun heats up the room or raised in the event of frost.
The frogRelay2-2-PF could also be used to intelligently control the sockets ina socket circuit limited to 6 A.
The frogs can be controlled with the frogblue HomeApp via smartphone or tablet (iOS and Android), frogDisplay, frogKey or simply via the conventional switch/button connected to a frog. We always recommend buttons, as the full range of functions can be used with individual and different touch patterns, such as double or triple clicks, etc.
Switch status feedback
Parametrisable switching on and switching off behaviour
Switch on and switch off delay
Mutual locking of outputs in motor mode/roller blind mode (configuration using the frogblue app)
Mains supply via power cable, no additional cabling required between frogblue modules.
For assembly in device sockets according to DIN 49073. Socket depth minimum 53 mm when installed behind switch insert, individual installation is required at lower depth. A socket depth of 63 mm is recommended.
This device is a product of the frogblue system. Detailed technical expertise obtained through frogblue training sessions is a prerequisite. The functionality of the device depends on the software. Detailed information regarding software versions and the respective range of functions can be found on the frogblue website. Technical descriptions, additional detailed instructions as well as notes, information regarding proper disposal can be found in the manual, which is available on the frogblue website. Commissioning and configuration will be executed using the frogblue app.
Electrical devices may only be installed and assembled by qualified, skilled electricians. Failure to observe the instructions can cause damage to the device and result in fire and other hazards. Danger caused by electric shock. Before starting work on the device or replacing light sources, always disconnect the power supply and switch off the circuit breakers. When SELV voltage is connected to one output (A or B), then only maximum SELV voltage may be connected to the other output (B or A). Country-specific regulations must always be observed.
Once the user has seen at least one product this snippet will be visible.
Recently viewed Products
To install this Web App in your iPhone/iPad press and then Add to Home Screen.